 Hello friends, I hope all of you are fine. In today’s tutorial, we are gonna have a look at Synchronous Generator Operating Alone. The performance of the synchronous generator with different load relies on the P.F of the load and the at its working conditions either it is working separately or with some other generator. There are many factors that affect the working of the synchronous generator.

In today’s post to see the operation of the synchronous generator, we will construct a phasor diagram and will observe the effect of the armature resistance RA. so let’s get started with the Synchronous Generator Operating Alone.

#### Effect of Load Changes on a Synchronous Generator Operating Alone

• As the field windings resistance is not varied, so field current also has same value due to these two constants the flux generated by the field current also constant.
• Subsequently, the prime mover also moving the rotor of the generator with the same velocity.
• As the field current, flux, and field resistance all are constant, so the internal generated voltage EA will also constant.

EA= Køw

• As the internal generated voltage is constant, if we vary the load and find the effect of the variation in the load we will draw different loads phasors diagram and discuss them.
• To study variation effect of the load we connect three different loads inductive, capacitive and resistive. Then see their results by phasor diagrams.

#### Synchronous Generator working with Inductive load

• As the generator is connected with the inductive load its power factor will be lagging.
• If we increase the amount of the load connected at similar P.F, due to increment in the load the armature current also increases, but its angle ø with the terminal voltage Vø has similar value as before changing.
• So, the armature reaction voltage jXsIA also increases but still has a similar angle as before load increment.

EA = Vø + jXsIA

#### Generator working with Capacitive load

• Let’s suppose now the load connected with the generator is capacitive. The value of the phase voltage will increase this time. You can see the capacitive load effect in a given figure.

#### Voltage Regulation of the Synchronous Generator

• We can very easily compare the voltage performance of the 2 generators by their voltage regulation.
• The formula of the voltage regulation is given here.

VR = [(Vnl – Vfl)/ Vfl] x 100%

• In this equation, Vnl is the no-load voltage of the generator and the Vfl is the rated voltage of the generator.
• If the synchronous generator is connected with the inductive load its voltage regulations are highly positive.
• If the load is resistive then the voltage regulation is less positive.
• If the load is capacitive then the voltage regulation is negative.
• Usually, it is necessary to maintain the voltage level provided to the load, either load itself is changing or not.
• To keep voltage constant changes the internal generated voltage if the load is changing.
• As we know.

EA= Køw

• As the speed is constant so we can control internal generated voltage by speed changing, an option is to vary the flux of the rotor.
• Let’s take an example, let’s assume that the inductive load is connected with the generator. As we have discussed above terminal voltage will decrease with the increase of the inductive load.
• To again maintain the voltage to last value, decrease the field resistance.
• The decrement in the field resistance will increase the field current, which increase the flux.
• Flux increment will increase the internal generated voltage EA, which will increase the phase voltage and the terminal voltage.

#### Synchronous Generator Operating Alone Summary

• We can summarize this explanation as.
• The decrement in the field resistance will increase the value of the field current.
• Increment in the field current will increase the flux.
• Flux increment will increase the internal generated voltage EA.
• Increment in the internal generated voltage will increase the phase voltage.
• If you have to decrease the terminal voltage, then do all the steps from last to first. It is very easy to maintain the terminal voltage with the change in the load by just controlling the field current.

You can also read some related topics to synchronous generator that are listed here.

Introduction to Synchronous Generator

Synchronous Generator Equivalent Circuit

Synchronous Generator Phasor Diagram

Synchronous Generator Power and Torque

Synchronous Generator Parameters

Synchronous Generator Parallel Operation

Synchronous Generator parallel with Large Power system

Synchronous Generator Parallel with same Size Generator

Synchronous Generator Ratings

Synchronous Generator Capability Curves

Synchronous Generator Transients

That’s all about Synchronous Generator Operating Alone if you have any question about it ask in comments. See you next tutorial Parallel Operation of Synchronous Generator.

# Free SMT Assembly Monthly

New arrival for Aluminum boards, only \$2